The workshop LED high bay lighting project in Bulgaria, was finished in 2016. We chose about 150 units of 150W ZGSM HB series LED high bay lights to get an average lux of over 300lx. The color temperature of 4000K makes the color of the light more comfortable for our eyes. The 60-degree angle lens makes the light of our fixture more concentrated to the area we need to illuminate without glare. ZGSM HB series high bay lights are modular designed, which is easier to install and maintain. It's available to be applied to warehouse lighting, factory lighting, workroom lighting, gymnasium lighting, garage lighting, and so on.
Product: 150W LED Highbay Lights
Model No.: ZGSM-GCD150H5B
LED: Lumileds 3030
Optics: 60 degrees
QTY: 150 Units
|LED Brand||Lumileds LUXEON 3030/5050|
|Driver Brand||Meanwell HLG series|
|LED Module Quantity||3 modules|
|Lamp Rated Luminous Efficiency||130-160 lm/w|
|Lamp Rated Lumen output||19500-24000 lm (Lumen tolerance +/- 5%)|
|Color Rendering Index||70 (80 is optional)|
|Color Temperature||3000K, 4000K, 5000K, or 5700K|
|Photometric Type||60,90,110 degrees|
|Optimal Operating Temperature||25℃|
|Working Environment||Between-40°C~+50°C, 10%~90%RH|
|Total Harmonic Distortion||< 10%|
|Lumen Maintenance||> 100,000 hours -L70, @25 ºC (77 ºF)|
|Protection||Class I ( Class II optional)|
|Certification||CE, ROHS, LM80|
|Dimming Options||1-10V or DALI or PWM or Timer|
|Control Options||Motion sensor or Smart control|
|120W Modular Design High Bay Lighting||DLC Listed 120W UL Certified High Bay Lighting||160W UFO High Bay Light|
|IP66 IK10 160w UL High Bay Light||Suspended 120W High Bay LED Lighting||150 Watt UFO High Bay LED Light|
|LED High Bay Light Project in Hungary||LED High Bay Light Project in UAE||LED High Bay Light Project in Italy|
|LED High Bay Light Project in Spain||LED High Bay Light Project in Croatia||LED High Bay Light Project in Netherlands|
|What Is a High Bay Light and Its Purpose?||Guide to Buy Led High Bay Light||What Are The Advantages Of Led High Bay Light ?|
|How To Replace & Repair Industrial Workshop Light?|
For bright light, a spacing of 15 feet can be utilized at a height of 20 feet, and for average light, an 18-foot spacing should be used. You can go for a 20-foot spacing between the lights at 30 feet height to get a brighter light. For regular lighting, however, a 25-foot separation is sufficient.
Reflectors or lenses are used in low bay lighting fixtures to disperse light and reduce glare. To make the light flow down to the floor, a high bay light fixture requires specific reflectors made of aluminum or prismatic components to scatter the light and illuminate shelves and other higher objects.
Depending on how the existing lighting configuration is configured, there are a variety of approaches to retrofit lighting systems with LEDs. In many circumstances, replacing the existing fixture with a new LED fixture that produces a comparable lumen output is the simplest and most basic solution.
In other cases, reconfiguring a complete lighting system plan to effectively update to LED technology may be necessary. There are a few cases when an LED retrofit kit can be used to update an existing fixture, but this requires some electrical knowledge to execute successfully.
Copyright © Hangzhou ZGSM Technology Co., Ltd. All Rights Reserved